The Inova PIR is a modern exterior wall light which is finished in matt black, and is ideal for use in both domestic and commercial application. The addition of a PIR sensor means it is activated on movement making it suitable for lighting paths and doorways and for use as a security light. Also available in Brushed stainless steel (304) code 49945.
The colour of a lamp is defined as a measurement called kelvins. A standard GLS light bulb in your house would be 2,700 kelvins which is in the warm colour spectrum and a lamp with 5,000 kelvins would be at the very cold white spectrum. Getting the right colour temperature of a lamp does matter as the warm colour wavelength helps to soften the tone of the area and gives a warm soft relaxed feel and ideal for colourful flower beds and rockery areas especially with wooden bark and at the other end of the scale a 4,000 to 5,000 kelvin lamp colour would be used against a light background such as white walls or to accentuate grey blueish foliage in shrubs and small trees. When you buy a new, energy efficient bulb, keep your application and colour scheme in mind and make sure to buy the bulb with a colour temperature to match.
Existing fittings must be completely removed before installation of a new product. Before removing the existing fitting, carefully note the position of each set of wires.
Remove mounting box (A) from product by removing dome nuts (C) and washers (D). Carefully pierce a small hole in the rubber gasket in the centre of the mounting box to allow the cable to pass through. Thread the cable through the hole, ensuring the drain hole is at the base of the mounting box.
Fix the mounting box to the wall using the screws and plugs supplied (B). Ensure the wall is capable of holding the weight of the product. Take care to avoid damaging any concealed wiring and pipes. The correct fixings should be used for brick or cavity walls. Seal the screw fixings to maintain the IP rating of the fitting.
Having correctly identified the wiring from your existing light fitting, pull the wire through the hole and connect to the connection block inside the product.
Ensure that the cable is not snagged and seal to maintain the IP rating of the product. Fit the product back on the mounting box and refit washers (D) and dome nuts (C) tighten dome nuts to secure. Replace fuse or circuit breaker and switch on. Your light is now ready for use.
The unit must be installed in a vertical position, and fitted 1.8m above ground. The PIR sensor can be adjusted, allowing the detection distance to be altered to suit the location. The detection angle is set at 110 degrees. The duration that the lamp stays on can also be altered from 5 seconds - 5 minutes. Use a small screwdriver to adjust the 'Time' and 'Sens' screws. When adjusting the sensitivity (detection distance) in daylight it will be necessary to cover the sensor to simulate night time.
|colour:||Black, stainless steel 304|
|IP rating:||IP 44|
|Materials:||stainless steel 304|
|Sensor_Description:||110 degree detection angle, 8m maximum range with a 10 sec - 10 min timer function|
|Material Finish:||Brushed stainless steel & clear pc, Matt black paint & clear pc|
|additional information:||Not suitable with a dimmer switch|